Fitting Underfloor heating in large areas
How to fit underfloor heating in large areas
Underfloor heating thermostats have a limit to the power they can switch. Our thermostats have a limit of 16amps or 3600 watts. This effects larger areas because the load often exceeds this limit.
By choosing a different heating mat for example, a 150w system will have less wattage than a 200w system. This will alter the load on the thermostat and may solve your problem right off the bat.
For areas that still exceed the limit
For areas that exceed the limit there are two options available.
- Split the area into 2 zones.
- Install a contactor. A contactor or relay is a switch that is capable of switching high loads. Your thermostat would switch the relay or contactor on or off rather than the the heating. All the heating power supplies run back to the contactor switch.
Still unsure? Not a problem. Give our technical team a call on
KEEP AN EYE OUT !
From time to time we add new fantastic products and offer some fantastic deals
Free Next Day Delivery
No Better Price
Price Match Promise
On Selected Products
30 Day Returns
No Quibble Returns
© Copyright Living Heat Ltd 2019 – Registration No: 5466356 – VAT No: 861161442